ID-8846 Keywords or Part Number(s): 002457The smallest split system unit available, generally suitable for pop tops up to 17' with 2.2kws of cooling and 1.5kw of heating.
The air handler (evaporator) has manual controls and is installed in the overhead cupboard, the compact condensor unit will fit under a dinette/seat or bottom of cupboard providing fitting flexibility.
normally suitable for caravans, motor homes and pop tops up to 5.2m (external dimension)
supplied with a low profile condenser that can normally be fitted under beds and seats without increasing height
able to give year round comfort with its ventilating, cooling and heating modes
provides a heater element style warmth. This means quieter running noise and the ability to run in freezing ambient temperatures without any need to de-ice frozen coils
fitted with easy to use controls.
Electrical rating: 240V,50hz
Nominal cooling capacity: 2.2kw
Nominal heating capacity: 1.5kw
Maximum rated current, cooling: 4.0A
Maximum rated current, heating: 6.5A
Locked rotor current: 18A
Inside Air Delivery, Maximum: 110l/s
Installed Weight: 36kg
Condensor Height: 245mm
Condensor Width: 642mm
condensor Depth: 450mm
Air Handler Height: 240mm
Air Handler Width: 380mm
Air Handler Depth: 250mm
Minimum cupboard dimensions required 490mm Wide x 290mm High x 310mm Deep
All products from Caravans Plus come with a guarantee. This one comes with a 12 months manufacturer's warranty.
Click to View Product Manual (220kb) Click to View Product Brochure (258kb)
Selecting the correct Air Conditioner
The Heron are NOT suitable for installation by the DIY installer due to the requirement of making refrigerant lines.
In most states of Australia it is a requirement by law that connection of refrigerant lines be carried out by a licensed tradesperson.
The installer will place the Condensor unit usually on the offside of the RV resting on the floor or above a strengthened wheel arch.
The Air handler is placed in an upper cupboard up to 5metres away from the Condensor.
All wiring is included.
The installer must then make 2 copper pipe refrigerant lines with flared ends (flaring instructions are included BUT pipes are NOT included) one being 1/4" and one being 3/8" dia copper pipe (the 3/8" pipe must also be insulated).
After fitting pipes the pre-charged Condensor is purged following the appropriate instructions depending on the State/Country laws that are applicable. In some State/Countries a vacuum pump will be required to adhere to the applicable laws.
Leak testing of all connections is also carried out by the recommended methods.
We have been selling this product, or an earlier model, for around 12 months now. We get them in from our supplier as soon as someone orders one. These will only be sent by Courier. Due to either size, weight, or other reason. PO. Boxes are not permitted for large items.